Analysis of common faults of oil immersed transformer:How to reduce the failure of dry-type transformer?BAM,Accurately measure the resistance of each phase winding and carry out the measurement. If there is a great difference, it is a common fault of the winding. Then carry out the appearance inspection of the iron core, and then accurately measure the inter chip insulation resistor by AC voltage and galvanometer method. If the damage is not large, paint the damaged part.Wiring mode of dry-type transformer:Mineros,Turn off the gate valve (butterfly valve) of the left and right tablet computers of the heat pipe radiator to isolate the oil in the heat pipe radiator from the oil in the tank, so as to reduce the working pressure and leakage. After the leakage location is determined, appropriate surface treatment shall be carried out, and then Fushi blue raw materials shall be selected for sealing treatment.Oil leakage at electric welding positionGradually, high-frequency vibration damping mechanical equipment, such as low-frequency vibration damping platform, is installed at the bottom of the dry-type transformer, which can reduce the downward dispersion of the vibration of the dry-type transformer. Then replace the connection between the dry-type transformer and the surrounding engineering buildings roads, etc. with flexible connection, or use elastic yellow shock absorption mechanical equipment to prevent the vibration from spreading according to the rigid connection. If possible, the dry-type transformer room can also be soundproofed and decorated, and sound-absorbing plates and silencing shutters can be used to improve the soundproofing capacity of the dry-type transformer room.
In the whole process of transmitting electromagnetic energy in the power supply system, the voltage loss is inversely proportional to the voltage, and the output power loss is inversely proportional to the square meter of voltage. The transformer is used to increase the voltage and reduce the closing damage.Principle of step-up dry-type transformer: the step-up dry-type transformer is a component that correspondingly converts low communication AC voltage,BAMNational standard for oil immersed transformer, large current flow and small characteristic impedance into high communication AC voltage, small current and large characteristic impedance. When there is an AC circuit in the original coil, the communication AC magnetic flux will be caused in the transformer core (or magnetic core), there is more noise, and some even cause noise,In specific daily life the dry-type transformer needs sound insulation treatment. There are many processes and key methods to deal with the noise of the common dry-type transformer. How should the noise of the dry-type transformer be solved? Or with the dry-type transformer manufacturer's network editor to simply understand it.Design brand, we have a certain understanding of the optical wavelength of oil immersed transformer. What kind of function does it have for transformer?The power transformer conductor refers to the connecting transmission line between each electromagnetic coil, between the electromagnetic coil and the group outlet pipe, and between the electromagnetic coil and the tap changer.It is generally made due to unreasonable installation or ineffective sealing. Polymer composite materials can bond metal materials, porcelain, laminated glass and other materials very well, so as to achieve the pressure management of oil leakage.
The raw materials of Fushi blue can be used for bonding,BAM4000 dry type transformer size,BAMTransformer and box type substation, so that the overall oil leakage of the connector can be greatly controlled; If the actual operation is convenient, the metal shell can also be bonded at the same time to achieve the purpose of leakage treatment.Installation material list,What about oil immersed transformer fire?The proper selection of Anhui dry-type transformer has a key effect on improving the safety and smooth operation of power system software. In the above original text, we have already mastered the structure and characteristics of dry-type transformer. In this part, we will describe how to select dry-type transformer according to the load characteristics and application environment of dry-type transformer.Manufacturing process and steps of dry-type transformerBAM,Deterioration damage of transformer core insulationAfter tightening the loose bolts seal the flange, and solve the bolts that are likely to leak, so as to achieve the goal of complete treatment. Tighten the loose bolts strictly according to the actual operation and processing technology.The zero line is mainly used in the working circuit. The voltage caused by the zero line is equivalent to the line resistance multiplied by the current of the working circuit. Because of the distance, the voltage caused by the zero line can not be ignored. As a countermeasure to maintain life safety, it is more and more unreliable. Ground wire (PE): it is not used as a working circuit, but only as a maintenance line. Use the affirmation of the earth & ldquo; ” Voltage. When the machine and equipment casing is electrified, the current will be quickly grounded. Even if there is a lead for the PE line, it will be grounded from the surrounding grounding body.