The bearing capacity of each load is different. Generally dry-type transformer should operate under rated capacity, while oil transformer has better load working capacity.Gradually, such as low-frequency vibration damping platform, is installed at the bottom of the dry-type transformer, which can reduce the downward dispersion of the vibration of the dry-type transformer. Then replace the connection between the dry-type transformer and the surrounding engineering buildings, roads, etc. with flexible connection, or use elastic yellow shock absorption mechanical equipment to prevent the vibration from spreading according to the rigid connection. If possible, and sound-absorbing plates and silencing shutters can be used to improve the soundproofing capacity of the dry-type transformer room.Cherefteo,According to statistics, to occupy the main global technical position, the transformer industry depends on two key data, commodity volume and voltage level. As early as & ldquo; Eleventh Five Year Plan; In the early stage, China has been a powerful country in the production, manufacturing and application of dry-type transformers all over the world, but it is not a big country.Performance and main parameters of common metal composites, various welding processes and machinery and equipment, preparation treatment of thick steel plate, blanking process, production and manufacturing process and quality standards of automobile oil tank, riser, welding leakage test and NDT technology, surface treatment process and quality standards, Production process and quality standard of aluminum shield; Body suit iron insertion process, wire installation process, body dryness solution and dry transformer oil solution process, vacuum pump oil immersion, general installation process, leakage test and leakage detection process and quality standards. Performance parameters of key work clothes, machinery and equipment of each process flow; The natural working environment is basically regulated.Panalanoy,Deterioration damage of transformer core insulationThe power transformer is designed according to the temperature protection scheme. The embedded parts in the material layer of high (low) pressure electromagnetic coil poured with integral concrete are provided with longitudinal ventilation duct, which can be equipped with air-cooled machinery and equipment (cooling centrifugal fan). After selecting air-cooled machinery and equipment, the output capacity can be increased by %.Dry type transformer
Sound insulation treatment of main engine room the key to sound insulation treatment of dry-type transformer room is to start from three levels: window,CherefteoCommercial power transformer, ventilation and air exchange port and road surface, silencing cylinder, floating concrete floor damping pad and other sound insulation and noise reduction commodities to achieve sound insulation effect.The selection shall be carried out according to the load characteristics of power. There are many types of power loads. Different dry-type transformers shall be used for different power loads. If the standard impulse level of power load is less than kV, class H dry-type transformers shall be used. If the standard impulse level of power load exceeds kV, epoxy resin adhesive shall be used to pour dry-type transformers.Dry type transformer manufacturerRecommendation and consultation,The method and whole process of taking oil sample of power transformer are as follows:In relay protection dry-type transformer, the disconnection of the fault point is related to each other. In a word if there is any problem at a certain point, it will affect the whole power circuitNoise pollution control and prevention measures of dry-type transformer
Wiring mode of dry-type transformer:system,If you want to check the activated carbon fiber for the hanging cover, first take out the low-voltage waterproof sleeve and the on load transformer power switch, then lower the bell cover anchor bolt of the large cover, slowly hang the galvanized steel wire rope with sufficient lifting net weight on the commonly used earrings, wear round steel from top to bottom in the surrounding screw holes, and count the spacing and specifications for easy reinstallation. At the same time, the cable wind shall be added on all sides to ensure that the core international body will not be damaged during the whole lifting process. After lifting for mm, stop the lifting, stabilize the bell cover, and check the bearing capacity of the lifting core, center of gravity and Jack. After everything is normal, lift it again until the bell cover exceeds the relative height of the body, and rotate the crane to place the bell cover on the clean skid.The visual inspection method is that the staff use human eyes to observe the appearance change of the visible parts of the operating equipment to find the abnormal conditions of the equipment, such as discoloration,CherefteoCode for installation of power transformers, deformation, offset, cracking, loosening, ignition smoke, oil leakage broken strand disconnection, short-circuit fault marks, hanging of dirty things, etching and turbidity, which can be inspected according to the visual inspection method. Therefore visual inspection is one of the common methods of equipment inspection.The raw materials of Fushi blue can be used for bonding, so that the overall oil leakage of the connector can be greatly controlled; If the actual operation is convenient, the metal shell can also be bonded at the same time to achieve the purpose of leakage treatment.Cherefteo,Avoid aging and damage of power transformer iron core insulation: aging of iron core insulation or damage of waterproof sleeve holding anchor bolt will cause large vortex of iron core, and long-term scalding of iron core will lead to insulation aging.Avoid the load operation of power transformer: if the load operation is long-term, it will lead to the scalding of solenoid coil, slow aging of insulation, short circuit fault between boxes, two-color short circuit fault or short circuit to ground fault and dissolution of oil.& ldquo; YN,CherefteoThree winding power transformer, D & rdquo;, in which indicates that when the working voltage phasor of the primary side line as the minute hand, refers to the position at o'clock, the phase voltage phasor of the secondary side is at o'clock. That is, the phase voltage UAB of the secondary side lags degrees behind the working voltage uab of the primary side line (or degrees ahead).