Water flow into the bearing damages the bearing. Under the action of auxiliary devices, it can transport the slurry, and because the sealing device itself is special, it can also ensure the internal and external balance of the submersible slurry pump during transportation, Determination of flow Potential is convenient and flexible. It is easy to operate. It can be operated by a fool who turns on the power supply under immersion; It has a wide range of applications. In many cases, it belongs to a portable workstation, which can be brought wherever it is needed, because it does not need too many auxiliary facilities.Dolores,Port TolstoyCirculating hot water pipeline pump, The vertical sand pumping pump is popular with a wide range of sand pumping pump users because it is easy to move. This equipment is made of high-tech endurance data. Its service life has been greatly improved, and the maintenance frequency has been reduced,Port TolstoySubmersible non clogging slurry pump, the cost has been reduced, and the income has been increased. It is not correct that it has no effect on us. Reasonable.
When adding lubricating oil to the pump at ordinary times,Port TolstoyDeep well pump, the metering must be controlled, and the excess lubricating oil in the pump must be discharged and replaced regularly. absorb various solid slurry products processed by various coal water slurry operations. First of all, lets understand the causes of insufficient liquid supply: If the liquid level stored in the circulating liquid storage tank is lower than %, then insufficient liquid supply will occur when it is in use. Or the pump adds too much lubricating oil, which leads to accumulationplan, The fruit is also bad; When the axial flow pump is used, but the head is not too high, so the effect of using the submersible slurry pump in many plain areas is also relatively good; The water output and head of the mixed flow pump are actually derived from one The balance ring is also disassembled; Then remove the last stage impeller and the key back, and the middle section including the guide vane; in addition, remove the impellers, but when it is serious, it will directly burn out the insulation; There may also be some faults in the ventilation system. At this time, it is necessary to check whether the fan of the submersible slurry pump is damaged or rotating
Rotate in the rolling direction until the friction between the impeller and the front guard plate stops, then use the adjusting bolt to move the rotor backward, record the forward and backward movement gap, evenly distribute it between the front and rear guard plates of the impeller until the gap between the impeller, the front guard plate and the rear guard plate is flat, stop, and tighten the two dust discs and fasten them on the shaft. adjustmentmanagement, Ordinary vertical motor can be used without waterproof, while the motor shaft and pump shaft of submersible slurry pump are coaxial so the motor must be waterproof and sealed, and the motor and pump can be immersed in liquid at the same time; The vertical slurry pump is an early product, and the submersible slurry pump is a newly developed product according to the market demand Secondly, lets talk about the difference between WQ and QW sewage pumps. In addition, the use of ° and S-shaped bends should be reduced as much as possible during the installation and design of pipelines.Port Tolstoy, During adjustment, firstly loosen the support cover, then compress the nut, and then loosen the bearing seat. After adjusting the screw, tighten the compression nut of the bearing seat evenly to make the assembly move towards the pump head. It is necessary to turn the trolley while tightening until the plate does not move. Rotate according to the pump operation No matter what type of slurry pump you need Ritter pump will provide you with high-quality slurry pump products; New progress in submersible slurry pump technology in recent years The diving depth has increased from meters to meters! The bus voltage where the motor is located is V. Due to the uneven cable voltage drop and load distribution, it is also possible that the temperature is too high due to the low voltage of the water pump.