For example, in the s, the radio programs applied by every family in the countryside had a ground wire, and they were often wet with tap water. Protective grounding is to bury the copper plate of metal electrical conductor in the soil layer, and then lead a point of it out of the road with transmission line, which completes the grounding protection. The grounding wire specifies the grounding wire resistance ≤ Ω. Grounding protection is a safeguard measure adopted to avoid safety accidents when using household appliances, office and other electrical equipment.The oil in the machinery and equipment of the oil storage tank shall generally stand for more than h before sampling; it is not necessary to stand when sampling on the running power transformer.Birmingham,BirminghamPrice of dry-type transformer,BirminghamTransformer and current,When the output power P of the transformer is equivalent to the input power P, the efficiency & ETA; Equivalent, the transformer will not cause loss. But in fact, there is no such transformer. The electromagnetic energy of transformer always causes loss. The key of this kind of loss is copper loss and iron loss. Copper loss refers to the loss caused by the number of turns of transformer coil. When the current has a fever according to the number of turns of the coil, part of the electromagnetic energy changes into energy and is lost. Because the electromagnetic coil is generally wound by copper core wire with insulating layer it is called copper loss.The tap changer of power transformer shall also have strong insulation. kV off load tap changer is generally insulated from the ground by the produced insulating paper pipe factory.Panaoti,Manufacturing process and steps of dry-type transformerWith the rapid development of society and the continuous development trend of computers, the calculation of data in the whole process of oil immersed transformer wave has long had results. Only effective selection of calculation entity models and methods is needed, the accuracy of calculation conclusions can meet the needs of architectural design, and scientific and reasonable data method is selected, Not only can the current distribution of the oil immersed transformer be clearly defined in the development stage, but also the winding and other structures of the oil immersed transformer can be effectively arranged and distributed in a certain scope, which greatly facilitates the design scheme of the oil immersed transformer and ensures the stability of operation.Careless maintenance and insulation damage
Protective measures for damping of dry-type transformerThe insulation between silicon steel sheets is damaged, resulting in overheating and melting of the iron core;When leaving the factory,When the power transformer operates at full load, it needs a large reactive load. This reactive load shall be provided by the power supply and distribution system. If the transformer volume is too large, it will not only increase the initial project investment, but also make the transformer operate at full load or load for a long time expand the proportion of full load loss, reduce power factor and increase Internet loss. Such operation is neither economic development nor scientific.Equipped with a temperature controller, platinum thermistor (pt) is placed beside the embedded hole on the top of the low-voltage solenoid coil to test the winding resistance temperature rise of the transformer, stop the cooling centrifugal fan, set up common problem alarm, overtemperature alarm and overtemperature tripping effect, and provide reliable overvoltage protection machinery and equipment for the dry test transformer, so as to test the safety performance of the transformer operation.Use fiber materials to seal the bolts to achieve the goal of controlling leakage. The other is to screw out the bolt (nut), wipe the Fushi blue film remover on the surface, and then tighten it after wiping the raw materials on the surface. After drying, the treatment goal can be achieved.
The manufacturing process of dry-type transformer is very process,The method and whole process of taking oil sample of power transformer are as follows:The transformer manufacturer said that the temperature display equipment: the temperature change value is measured according to the PT temperature sensor embedded in the bottom voltage winding to immediately indicate the winding temperature of each phase (three-phase safety inspection and Zui large value indication, and the historical time Zui high temperature can be recorded). The Zui high temperature can be input and output as mA analog quantity. If it is to be far away (the distance can reach m, the electronic computer can be equipped with an electronic computer socket, and transformers can be detected. The over temperature alarm and trip of the system software can also be signaled by the resistor data of Pt thermistor sensor,BirminghamSCB dry type transformer model, so as to further improve the stability of the temperature maintenance system software.When the whole process of winding wave of oil immersed transformer is calculated by using the marking method, the winding of oil immersed transformer is generally divided into multiple modules, and each module is replaced by an equivalent circuit and its power circuit includes an inductance and vertical capacitance, a capacitance to ground or capacitance between windings, They also have mutual inductors between the inductors of each module, and collect the chain Internet as the equivalent power circuit of oil immersed transformer. The precision of the conclusion can completely meet the needs of practical projects.Birmingham,Power transformers are also used for testing, which are called test power transformers. They can be divided into inflatable, oil transformer, dry test and other test power transformers. They are the basic test equipment for communication AC compression test for many consumers such as power stations, power supply bureaus and scientific research institutions. According to the specifications of the Bureau of quality supervision, It is used to carry out insulation compressive strength test under required current for various electrical products, electrical components and insulating raw materials.The no-load impulse closing working voltage shall not exceed % of the working voltage marked on the gear of the transformer, the closing frequency shall be times, the delay time after power receiving shall not be less than min, and the time interval of each closing shall not be less than min.Sound insulation treatment of main engine room the key to sound insulation treatment of dry-type transformer room is to start from three levels: window, ventilation and air exchange port and road surface, and apply sound insulation window silencing cylinder, floating concrete floor damping pad and other sound insulation and noise reduction commodities to achieve sound insulation effect.